Topics: water quality, water treatment, water plant, media packing, ION Exchange Resin, RO system, Pressure filter, Sand filters, Filter Media, industrial facilities, green sand, Gravity Filters, Constructed Wetlands
Per-and polyfluorinated substances (PFAS) have been used for decades in many consumer products, and they are man-made and have a high residual time in the environment. These chemicals are used for various purposes, including nonstick surfaces, heat protection of circuits, water resistance, fighting fire as they are utilized in fire depression foam, and many other industrial applications. The difficult thing about PFAS is that the very reason they work so well on so many manufactured products is why they are so challenging to get rid of or treat once they have entered the environment or water supply. PFAS are being more and more regulated, and requirements are being put in place by many states and agencies to require the treatment and removal of PFAS and safeguard and protect drinking water.
PFAS are soluble in water, and they are not a volatile organic chemical (VOC), so traditional treatment methods such as utilizing an air stripping tower or degasification system are not effective methods to remove PFAS. One of the first technologies to remove PFAS from drinking water and the environment is activated carbon absorption. In recent years, utilizing ion exchange resins has proven effective and is gaining popularity for the treatment method. Ion exchange resins attach and bond with the PFAS and remove it effectively from the water. Some chemicals tested and studied with success include perfluorooctanoic acid (PFOS). In addition to these technologies, reverse osmosis utilizing high-pressure membranes has an 80-90% effective rate and has proven to be technically efficient in removing PFAS. An R.O. process produces a concentrated waste stream.
electric motors are used for a variety of applications. These often include pumping water or other fluids, transporting material on conveyors or lifts, or providing motive force to moving parts of a mechanical device. The electric motor dominates the field whenever something needs to move. Regardless of the end use, all these motors will have one thing in common, a motor controller.
A motor controller is a device with the means to turn the motor on and off, provide circuit protection, and serve as a disconnecting means to render the circuit safe during maintenance. Traditionally, this is done with a direct-on-line (DOL) motor starter. A DOL starter installation consists of a branch breaker combined with a DOL motor starter and overload module. In a typical DOL motor starter installation, the branch breaker will serve as short circuit protection, as well as a means of electrical disconnect. The motor starter unit is essentially a large relay with a magnetic coil and high-power contacts held apart by springs. When the motor is called to run, the magnetic coil is energized, pulling in the contacts and bridging the line side to the load side terminals, allowing power to flow. Once the motor starter has contact, electrical power flows out through an overload disconnect module, and then to the electric motor. The DOL motor starter is a well proven design that is familiar to almost anyone in the industrial space and is still what is found in a majority of applications.
the removal of carbon dioxide (CO2). The need to remove (CO2) is essential in most Aquaculture, Municipal, Industrial, and Food & Beverage Processes To understand you must familiarize yourself with Henry’s Law.
Henry's Law defines the method and proportional relationship between the amount of a gas in solution
in relationship to the gases partial pressure in the atmosphere. Often you will see and hear various terms like degasification, decarbonation, aeration, and even air stripping when discussing the removal of dissolved gases and other convertible elements from water. Understanding the impacts that Carbon Dioxide (CO2) can have on both equipment and aquatic life provides the basic reasons why the need to decarbonate water, exists. Carbon Dioxide (CO2) can exist naturally in the raw water supply or be the results of ph control and balance. In either case the the process called Decarbonation or Degasification provide the most cost effective and efficient manner to reduce or tally remove (CO2) from the water. In addition to Carbon Dioxide (CO2), water can contain a variety of other contaminants that may impact the removal efficiency of the Carbon Dioxide. A variety of elements as well as dissolved gases such as oxygen, nitrogen and carbon dioxide (CO2). A full analytical review of the water chemistry is required to properly design and size the “Water Treatment” process.
Breaking the bonds in water to release a dissolved gas
such as carbon dioxide (CO2) you must change the conditions of the vapor pressure surrounding the gas and allow the gas to be removed. There are many variables to consider when designing or calculating the “means and methods” of the removal of carbon dioxide (CO2). When I refer to the means and methods. I am referring to the design of a decarbonator and its components. The means equals the size and type (Hydraulic load) of the decarbonator and the “method” equals the additional variables such as cubic foot of air flow (CFM) and “Ratio” of the air to water to accomplish the proportional condition needed to remove the carbon dioxide (CO2).
Topics: water treatment issues, degasification, pH levels of water, aeration, iron oxidation, water treatment, water plant, bicarbonate, hydrogen sulfide (H2S), pH levels, Decarbonation, ION Exchange Resin, dissolved gases, De-Aeration, wastewater, carbon dioxide, oxygen, decarbonator, degasifier, gases, carbonic acid, H2S Degasifier, removal of CO2 from water
The water treatment industry continues to develop and evolve and over the past two decades there have been many new developments in technology and even more refinement in existing technologies such as "Degasification". The evolution and advancement of water treatment have been driven by the constantly increasing demand from an increase in population that demand cost-effective solutions and recognition to improve safety with the implementation of NSF 61 standards.
All human cultures on our planet share a single commonality and that is the dependency on water to survive.
Many existing technologies such as "Degasification" have evolved with higher efficiency to meet the demand changes and provide safety to consumers and to the systems. Degasification refers to the removal of dissolved gases from liquids and the science to degasify water is based upon a chemistry equation known as "Henry's Law". The "proportionality factor" is called Henry's law constant" and was developed by William Henry in the early 19th century. Henry's Law states that "the amount of dissolved gas is proportional to its partial pressure in the gas". The most "cost" effective method to perform degasification is with the packed vertical tower called a "Degasifier” or “Decarbonator”.
The key words in this previous sentence for owners, operators, and engineers to focus on is "the most cost-effective" as there is no other process more cost-effective at removing dissolved gases at the lowest cost than the use of a Degasifier or decarbonator. The process of degasification is simple enough to understand. Water is pumped to the top of a vertically constructed tower where it first enters the tower through some type of distribution system at the same time there is a cross current air flowing up from the bottom by a blower located at the bottom of the tower and the air encounters the water and is exhausted at the top of the tower through an exhaust port. There are various types of distributions systems and we will explore these in later discussions. Once the water enters the top of the tower and passes through the distribution system it then travels by gravity downward. The next thing the water encounters is some type of media packing. There are various forms of media packing offered in the degasification industry and each type can offer higher performance or have the ability to deter fouling. The selection of the type, size, and volume is where the “experience, engineering and understanding of each application” comes in to play.
Topics: water treatment issues, water quality, degasification, pH levels of water, water treatment, advanced treatment solutions, About DeLoach Industries, water plant, NSF/ANSI 61, hydrogen sulfide (H2S), media packing, pH levels, scaling, caustic, Decarbonation, Safe drinking water, dissolved gases, carbon dioxide, decarbonator, boiler system, degasifier, carbonic acid, H2S Degasifier, Dissolved organic Carbon, co2 dissolved in water
On behalf of DeLoach Industries Inc., I would like to thank you for entering our drawing for the first annual "Clean Water Professional Appreciation Award". As you know we are celebrating our 60th year serving the water and wastewater Industry.
there are many types of different processes available to remove harmful minerals and gases from the water stream but the most effective process and most cost effective from both a capital investment and operational cost is a “Forced Draft Degasification System” (Degasifier).
Degasification is used in a wide range of water processes for industrial and municipal applications which extend from the production of chemicals to the production of semiconductors and in all applications the need to remove contaminants from the water and dissolved gases is key to achieving the end results needed in the industrial water process. Water from the ground often contains elements such as calcium carbonate, manganese, iron, salts, hydrogen sulfide, and sulfur just to name a few of the basic contaminants and these naturally occurring elements can cause serious damage and consequences to process equipment such as boiler systems, piping, membranes, and cation and anion exchange resins used in the demineralization process.
Calcium carbonate can dissolve in water under certain pH ranges forming carbonic acid and releasing carbon dioxide (CO2) gases. These gases are not only very corrosive to equipment like boiler feed systems and boiler tubes but also attack the actual resin beds found in cation and anion softening and demineralization system causing an increase in regeneration and chemical consumption and resin bed replacement.
By incorporating a Force Draft Degasification system you can remove dissolved gasses
like CO2 and hydrogen sulfide (H2S) to as low as 99.999% and improve the cation and anion system performance, extend the resin bed life, and lower the operating cost of the water treatment process.
Quite often Forced Draft Degasification is utilized “post” treatment to also remove newly formed dissolved gases prior to entering the boiler feed system to prevent corrosion damage within the tubes and feed system and pumps. These gases are easily removed with the forced draft degasifier at a much lower cost than chemical additives or liquid cell degasification that requires higher capital cost and much higher operating cost.
Topics: water treatment issues, degasification, pH levels of water, iron oxidation, water treatment, water distribution system, aluminum, water plant, odor control scrubber, hydrogen sulfide (H2S), calcium carbonate, media packing, pH levels, Langilier index (LSI), Decarbonation, ION Exchange Resin, dissolved gases, feed water, De-Aeration, wastewater, carbon dioxide, decarbonator, degasifier, carbonic acid, H2S Degasifier
The Term Sour Gas
refers to any natural gas or other gas that contains high levels of hydrogen sulfide (H2S). The H2S is typically naturally occurring and found in deposits of natural gas and when there are concentrations above 5.7 milligrams per cubic meter or 4 milligrams per cubic meter when tested under standard temperature and pressure. At these levels the industry classifies the gas as “Sour.” Of course there are variations to this classification dependent upon agency an organization.
A Sour gas is not to be confused with an acidic gas
although one could be both a sour gas is strictly defined by having large quantities of hydrogen sulfide and is usually accompanied by having mercaptans which adds to the foul smell and odor. The term is often used in the oil refinery business and when gases contain sour gas the process to remove the hydrogen sulfide and mercaptans is referred to as “Sweetening”. The most common method to “sweeten” and remove the sour gas is by processing the gas through an “amine process” which removes the harmful gas.
Topics: odor control, aeration, water treatment, advanced treatment solutions, biological scrubber, water plant, odor control scrubber, hydrogen sulfide (H2S), Chemical Odor, pH levels, Decarbonation, dissolved gases, wastewater, carbon dioxide, degasifier, gases, Amine, H2S Degasifier
DeLoach Industries made history in 1977 at the City of Cape Coral Florida water treatment plant with its large scale “degasification towers” connected to what was to become the first municipal water treatment facility in the United States to deploy the use of reverse osmosis on a large-scale production municipal treatment plant.
The Cape Coral water treatment plant for came on line in 1977 and produced 3 million gallons of water per day (GPD) or 11.35 liters of purified and treated water utilizing the “reverse osmosis” process. By 1985 the plant had expanded as it kept up with growth to produce 15 million gallons per day making it at the time the worlds’ largest “reverse osmosis” water treatment plant facility.
Topics: water quality, pH levels of water, water treatment, advanced treatment solutions, water plant, hydrogen sulfide (H2S), pH levels, Alkalinity, scaling, chlorine, caustic, Decarbonation, wastewater, carbon dioxide, degasifier, RO membrane, RO system, H2S Degasifier
There are many industries that require the use of a caustic scrubber which is considered a chemical scrubber and they range from the municipal industry, mining, semiconductor markets, pulp and paper and chemical refining. There is a wide variety of industrial processes that generate noxious or corrosive off gases that require treatment and a comparison is made about biological Vs. chemical. Often biological scrubbers have limitations due to concentrations, composition, or temperature of the contaminants and if the gas stream contains acid fumes then a biological scrubber is quickly ruled out.
The odor control selection is often fraught with choices of capital cost over operational cost and quite often comes down to familiarity from the designer or purchaser. It is always a good idea to freshen up on the industrial odor control the do’s and don’t’s before selecting the final solution. If the off gas source that needs to be treated is hydrogen sulfide (H2S) or some other type of gas stream produced by an acid or ammonia it will often require neutralization for human health reasons and to protect equipment or may be required to meet regulatory compliance. Caustic scrubbers may be either vertical or horizontal by design, but both utilize a packed media bed of either random packing or trays to allow the gas fumes to meet the recirculating caustic solution which then forces the reaction to occur.
Topics: water treatment issues, water quality, degasification, pH levels of water, odor control, water treatment, advanced treatment solutions, biological scrubber, water plant, odor control scrubber, hydrogen sulfide (H2S), Chemical Odor, pH levels, caustic, wastewater, carbon dioxide, degasifier, gases, caustic solution, sodium hydroxide water treatment